Outdoor boiler furnaces manufacturer and factory direct sales.
Stove Delivery And Installation
When you’re beginning to install your boiler, the footprint comes in handy to position the solid concrete blocks under the legs or pouring a concrete pad.
L = 60 inches
W = 44 inches
L = 48 inches
W = 44 inches
Those measurements are from the outsides of the stove’s legs. Each leg is approximately 3″ square. Therefore, the centered measurements for the EZ-Pro are 57″ x 41″, and for the EZ-Classic are 45″ x 41″. If you use these measurements when placing the solid concrete blocks and measure from the CENTER of each block, your stove should sit on them perfectly.
The factory installed check valve in the water pump needs to be removed and discarded prior to the installation of the pump.
A few tips to extend the life of your stove
A properly installed grounding rod system will protect people from electrical shock, help safeguard expensive electronic equipment, prevent electrolysis, limit neutral-to-ground voltage, and satisfy the NEC along the way.
Electrolysis of water is the decomposition of water (H2O) into oxygen (O2) and hydrogen (H2) gasses when an electric current passes through the water. Free oxygen in the water tank will promote rust formation and eventually cause catastrophic leaking and stove failure.
Use only a 4GA or larger wire with proper grounding clips. Grind paint away where the wire is attached to the stove to get a solid electrical connection.
An anode rod is commonly used on a water heater to prevent corrosion in the tank. It works for an outdoor boiler too. The easy way to install an anode rod in an Ezboilers stove is to add a tee fitting to the drain port (bottom port) on the back of the stove. The anode rod is then installed in the tee straight into the water jacket, and the drain shutoff valve is installed to the side of the tee. When you drain and flush the stove once every year, It’s a simple matter to remove the anode rod for visual inspection, and replace it when necessary.
GFI Outlet or GFI Breaker
Always use a GFI outlet or GFI breaker on the stove. This will protect the electronics, prolong the life of the stove, and protect the user from shock hazard as well.
Once a year during the off season, when the EZ Boiler is not in use, drain and flush the water jacket and refill it with water and a unit of sodium nitrite. Fill the water jacket completely to the top of the vent at this time so that all surfaces of the water jacket will be covered during the off season. This will help prevent rust and corrosion from attacking the top of the water jacket during the idle off season period. If significant amounts of water need to be replenished during the heating season, add enough additional sodium nitrite to maintain protective levels.
Coals and Ash
Pull the ash and coals to the front of the firebox before loading. Be sure to get right down to the firebox metal. This will improve heat transfer to the water jacket and reduce creosote build-up which could lead to creosote corrosion. Make it your daily practice to move the sides of the ash pile where it touches the firebox as well. An undisturbed ash line would allow creosote to build up in one spot, leading to corrosion. It is the number 1 cause of firebox failure. Empty old ashes periodically as needed.
Grease the Solenoid
The solenoid controls the air flow to the firebox. If it fails, there will be no control over the burn rate, and the stove won’t work. At least once a week, grease the solenoid shaft. As with any maintenance around the electrical, disconnect the power first. Clean off the old, dirty grease first, then apply a fresh coating on the solenoid shaft only. Use a Di-Electric grease on the solenoid shaft to prevent rusting and to allow free movement of the solenoid. A regular grease will also work if needed. This will extend the life of the solenoid, and keep the fire burning at the right rate.
End of Heating Season
Cover the chimney to prevent rain water from getting inside the firebox. Clean out all the ashes and optionally coat the exposed metal with a light coating of oil. This will prevent the firebox from rusting in the off season.
Very easy to work with once you know how. Here is a site with easy to follow directions and good instructional pictures. How to install PEX